10 AWG Solar Panel Wire SW0004 - 100 ft - UL 4703 Power Cable Black - Made in USA
|Conductor Size||10 AWG|
|Amps Per Conductor||40|
|Feet Per Pound||17.54|
|Conductor Material||Bare copper|
|Conductor Stranding||19 / 0.0234|
|Insulation Material||Cross-linked Polyethylene (XLP)|
|Insulation Thickness (in)||0.075|
|Minimum Temperature Rating||-40°C|
|Maximum Temperature Rating||90°CC|
|Nominal Outside Diameter (in)||0.23|
|Resistant to||Sunlight, ozone, UV, flame, and moisture|
|Agency Approvals||Type USE-2 per UL 854, RHH/RHW-2 per UL 44, Type PV per UL 4703|
The term "PV wire" (photovoltaic wire) is often used to refer to USE-2 or THHN wire, the terms are not interchangeable. PV wire is specifically rated in accordance with UL 4703. THHN wire is used as general building wire and lacks the construction and strength of specialized cables designated as UL 4703 or USE-2. Using THHN cable in place of either UL 4703 or USE-2 will result in failures.
Though USE-2 wire is impact and crush resistant, UL 4703 rated cable is superior to USE-2 in regards to low temperature flexibility, sunlight resistance, and flame resistance. PV wire for solar panels also has a thicker jacket and insulation than USE-2 wire. USE-2 cable is used in grounded PV systems only, which UL 4703 cable can be used for both grounded and ungrounded arrays.
View the quick comparison chart below for an overview.
Per the National Electrical Code, USE-2 wire is suitable for use in grounded PV arrays only. UL 4703 cable can be used within both grounded and ungrounded PV arrays. THHN cable is used as general building wire and cannot replace USE-2 or UL 4703 cable.
PV cable is rated for 90°C in wet conditions and up to 150°C in dry conditions. USE-2 is rated for 90°C in both wet and dry conditions. THHN cable is rated at 75°C in wet conditions and 90°C in dry conditions.
PV wire can be rated for 600 V, 1000 V, or 2000 V. THHN and USE-2 wire are only rated for 600 V.
PV wire is made up of stranded copper conductors, which makes it flexible. USE-2 wire is usually installed in locations where it is not subject to movement or mechanical damage, so they can use either solid or stranded conductors made of copper, copper-clad aluminum, or aluminum, making it less flexible than PV wire.
Insulation and Jacket
Both PV and USE-2 cable use thermoset insulation and jacket, typically XLPE (cross-linked polyethylene) or EPCV.
USE-2 cable is usually installed underground where it will likely not encounter flames, while PV wire can be exposed in an installation, so flames tests are required only for PV wire. Overload and mechanical abuse tests (including crushing and impact resistance) are applicable only to USE-2 cable.
PV wire must pass more stringent testing requirements for sunlight resistance and low temperature flexibility. It undergoes a 720 hour weatherometer and a -40°C cold chamber conditioning. In contrast, the requirements for USE-2 cable are 300-hour weatherometer and -25°C cold chamber conditioning.
- This Item: 10 AWG Solar Panel Wire SW0004 - 100 ft - UL 4703 Power Cable Black - Made in USA $40.00
- 10 AWG Solar Panel Wire SW0018 - 100 ft - UL 4703 Power Cable Red - Made in USA $40.00
- TEMCo RT3631 - 10 Qty 2/0 AWG 3/8" Hole Ring Terminal Lug - Tin Plated Copper $12.03
- TEMCo RT3621 - 10 Qty 2/0 AWG 5/16" Hole Ring Terminal Lug - Tin Plated Copper $12.03
- TEMCo RT3331 - 10 Qty 2 AWG 3/8" Hole Ring Terminal Lug - Tin Plated Copper $10.75